Adobe Flash Player(v16 or later) is required to view the catalog.
?Operable without the need to remove the unit from the rack
?Front access: Simple to control, service, and maintain with all filters
and drainage accessible via the front panel
?Space saving: Multiple chillers can be mounted to a 19-inch rack.
?Cooling capacity: 1.1/1.2/1.8/2.4/3.0 kW (60 Hz)
?Temperature stability: ±0.1℃
?Global power supply:
Single-phase 100 VAC (50/60 Hz)/115 VAC (60 Hz)
Single-phase 200 to 230 VAC (50/60 Hz)
|Cooling method||Circulating liquid|
5 to 35℃
15 to 35℃
Ethylene glycol aqueous solution (15%)
A precision temperature control method which utilizes expansion valves and temperature sensors allowed for the realization of a product with a high temperature stability of ±0.1°C.
Display of 24 types of alarm codes Operation is monitored at all times by the integrated sensor.
The applicable alarm code (24 types) is displayed after self-diagnosis.
When it is time for periodical checks of the pumps, fan motor, dustproof filter, etc.,
a maintenance code will be generated as a reminder. Helpful for facility maintenance
Thermo-chiller internal temperature, pressure, etc., can be displayed.
As the heating method uses discharged heat, a heater is unnecessary.
The heating function is effective in maintaining a constant temperature, particularly in the winter when the ambient temperature is low.
Serial communication (RS-232C/RS-485) and contact input/output signals (2 inputs and 3 outputs)
are equipped as standard. This allows for communication with the user’s equipment and system construction, depending on the application.
SMC has a comprehensive network in the global market.
We now have a presence of more than 500 branch offices and distributors in 83 countries and regions worldwide.
With this global network, we are able to provide a global supply of our substantial range of products and high-quality customer service.
We also provide full support to local factories, foreign manufacturing companies, and Japanese companies in each country.